|Specific gravity||ASTM D-792||1.2|
|Water absorption||ASTM D-570||0.15%|
|Tensile strength||ASTM D-638||60MPa|
|Elongation at Yield||ASTM D-638||6%|
|Tensile modulus||ASTM D-638||2,410 MPa|
|Flexural strength||ASTM D-790||96 MPa|
|Flexural modulus||ASTM D-790||2,410 MPa|
|Izod impact strength, Milled Notch||ASTM D-256||950J/m|
|Pencil Hardness**||ASTM D-3363||>6H|
|Erichsen Hardness**||ISO 4586-2 (DIN EN 438-2)||≥ 0.5N|
|Abrasion||ASTM D-1044||< 10 % Gloss|
|HDT 264 Psi, 1.82MPa||ASTM D-648||269°F (132°C)|
|CTE, -30°C to 30°C||ASTM D-696||0.65mm/36”/18°F
|Vicat softening point||304°F (151°C)|
|Continuous service temperature||212°F (100°C)|
|Max temperature, short term||302°F (150°C)|
* Internally tested by EGR
Lustrolite 100 is chemically resistant to the following substances:
Lustrolite should not be exposed the following substances:
The major building codes in the USA recommend NFPA 286, Standard Methods of Fire Tests for Evaluating Contribution of Wall and Ceiling Interior Finish to Room Fire Growth, for testing thermoplastics to be used as interior finishes.
This full-scale test is considered appropriate for determining the hazard of an interior finish (compared to the older ASTM E84 test methods), especially for certain plastics that can drip or melt and fall to the floor.
Lustrolite 100 complies with NFPA 286 requirements for interior finishes, however it is a combustible thermoplastic so appropriate fire precautions should always be observed.
|Properties||Test Method (DOT)||Requirements||Result|
|Flame spread||NFPA 286 – 2015 edition (2016)||Must not spread to the ceiling or the outer extremities||Meets criteria|
|Flashover||NFPA 286 – 2015 edition (2016)||Must not occur||Meets criteria|
|Peak Heat release||NFPA 286 – 2015 edition (2016)||Must be below 1,000sqm||Meets criteria|
|Smoke released||NFPA 286 – 2015 edition (2016)||Must be below 1,000sqm||Meets criteria|
|Flame spread rating||CAN/UL S102.2-10 (2018)||Class A = 0-25, Class B = 26-75 Class C = 76-200||25 (meets class A)|
|Smoke developed classification||CAN/UL S102.2-10 (2018)||Class A, B and C = < 450||370 (meets class A)|
|Burning behavior||UL94 (2008)||V-0**|
References to the product's performance under the testing standards above are informational only. Please consult qualified building professionals to ensure that the material is suitable and compliant for the chosen application as per local building code requirements.
** Refer to manufacturer data, Lustrolite 100 characteristics are taken from the CAMPUS plastics data bank and are based on the international catalogue of basic data for plastics according to ISO 10350.